Idea / Devices / Residual current breakers (RCBOs)
1P+N C6 RCBO 120-230V 10mA white
1P+N C 6 residual current breaker with overcurrent protection, supply voltage 120-230 V~ 50-60 Hz, IΔn 10 mA, breaking capacity 1500 A, white - 2 modules
3 - Active
|Question:||Why is it specified that the differential circuit breaker should not be used as a control 1-way switch?|
|Answer:||The product cannot be used as a control 1-way switch as it is designed to be installed upstream of a socket outlet or of a device for the sole purpose of permitting protection against overloads and the short-circuiting of the device itself and for the protection of the user against contact voltages; it is therefore an intended use that is completely different from that of a classic control 1-way switch, where the power supply interruptions towards the load occur according to the user’s desire.|
Didn't find the answer you were looking for?