Where do I connect and how do I set the parameters for the siren for outdoor use art.01715 and indoor use art.20496/19496/14496?
Any system sirens must be connected to the terminals +S INT (indoor siren) and +S EXT (outdoor siren) on the control panel. The siren parameters must be set in the section “Relays > Relay 1” in the By-alarm Manager software. In addition to the general parameters of “Relay 1” you must define which zones generate the relay in the event of active system unbalancing in “Activation by zone”.
Your portfolio is empty. Click on the icon in the product list to add a product.